The product image is for illustrations purposes and may not be correct. For more details please go to
manufacture's websiteor contact us.
Cable and Fuse Requirements:
Victron recommends the following cable and fuses for this product:
|Recommended DC Fuse||
|Recommended Cable Size (0-5m)||2 x 35mm²|
|Recommended Cable Size (5-10m)||2 x 70mm²|
The MultiPlus-II will prevent overload of a limited AC source, such as a generator or shore power connection. First, battery charging will automatically be reduced when otherwise an overload would occur. The second level will boost the output of a generator or shore side supply with power taken from the battery.
ESS: Energy Storage Systems
The MultiPlus-II is the key component in a Victron ESS system, providing the flexibility to combine with MPPT Solar Chargers or Grid-tie PV Inverters. For examples and more detailed information see the ESS (Energy Storage System) manual.
Uninterrupted AC power (UPS function)
In the event of a grid failure, or when shore or generator power is disconnected, the inverter within the Multi is automatically activated and takes over the supply to the connected loads. This happens so fast (less than 20 milliseconds) that computers and other electronic equipment will continue to operate without disruption.
Remote Monitoring and Control
Monitor and control your Multi and system or systems' locally (LAN) or remotely via the internet from anywhere in the world, using the free VRM app and freeVRM portalwebsite. Access can be from a phone, tablet, laptop or PC for multiple operating systems. There is no end to the level of control, via the required Color Control GX or Venus GX, from adjusting your Multi to auto starting a back generator and more...